DTB-L, DTB-AR and DTB-ART is a complex range of surge protection devices designed for protection of data, communication, measuring and control lines against surge effects. These surge protection devices are recommended for use in the Lightning Protection Zones Concept at the boundaries of LPZ 0A(B) - 1 according to EN 62305. All types provide effective protection of connected equipment against common mode and differential mode surge effects according to IEC 61643-21. The nomnal current of individual protected lines IN< 0,1A.
These devices consist of gas discharge tubes, series impedance and transils. The number of protected pairs is optional (1-4). These devices are produced for nominal voltage within the range of 6V-170V. DTB-AR and DTB-ART types are designed for the protection of equipment using DSL technology. Maximum discharge current of DTB-L is 20kA (8/20) and 2kA (8/20) for DTB-AR and DTB-ART types. For the protection of telephone lines it is recommended to use a type with nominal voltage UN=170V (with code mark “T”). The connection of protected lines is carried out by screw terminals for type DTB-L and by RJ45 connectors for types DTB-AR and DTB-ART.